[j-nsp] MX960 AC power strip
dickeypjeep at yahoo.com
Thu Aug 23 11:56:31 EDT 2012
The Juniper SKU for the MX c19/c20 power cord is CBL-MX-PWR-C19-C20 if anyone needed it.
From: joel jaeggli <joelja at bogus.com>
To: JA <mjaferabbas at gmail.com>
Cc: juniper-nsp at puck.nether.net
Sent: Thursday, August 23, 2012 9:08 AM
Subject: Re: [j-nsp] MX960 AC power strip
On 8/23/12 6:59 AM, JA wrote:
> I need advice if someone is having an MX960 up on AC power.
> Usually high capacity (32A) power bars (PDU) come with C13 or C19 outlets
> while Juniper has no provision for such power cords.
we use c19-c20 cables. we have a standard supplier for those so I don't
believe we're using a juniper p/n
the device (well the whole rack) is fed off two PDUs with a 30a 3 phase
service for each
> If European power
> cords are ordered with MX960, the CEE7/7 plug can be connected to Schuko
> outlets. But there is no Schuko PDU that supports more than 16A. One can
> easily exceed 16A if two power supplies are connected on same PDU.
> Can anyone recommend some alternative or if anyone faced similar situation?
> juniper-nsp mailing list juniper-nsp at puck.nether.net
juniper-nsp mailing list juniper-nsp at puck.nether.net
More information about the juniper-nsp